CellarPro 2000 VSx cooling units are self-contained and fully-charged. They are designed to be installed through and exterior wall and can be front ducted.
2000 VSs units can be located remotely from the cellar with the addition of front ducting (see add-on options above). With a front ducting hood or kit, this unit can be ducted up to 50 equivalent feet away from the cellar and 8" diameter ducting is recommended from start to end.
When calculating equivalent feet, each 90-degree turn is equal to 8 linear feet.
For installations where the unit is not inside the cellar, we offer a remote control and display kit which is wired to the cooling unit and can be placed inside or outside of the cellar.
If the fresh air intake (on the hot side) will pull air below 20°F, down to -20°F, you must add the fan cycling switch (see add-on options above).
The front of the cooling unit should never be situated in an area that will get below 32°F.
This unit must always be installed and operated in an upright position.
Become a Member
Earn points redeemable for discounts – even on your first order!